Watch that generator temperature An engine has to be warm to start
Generator manufacturers recommend an engine heater be installed on all automatic starting systems. This means gas or diesel, liquid cooled or air cooled. Some automatic heating method can always be arranged. The simplest is the coolant heater found on most generators.
Life Safety Code takes it a bit further:
If the generator is located inside a building, the generator room temperature may not fall below 50°F. NFPA 99, 1999 edition 3-126.96.36.199 (This is important for air-cooled and city water cooled systems)
If the engine is liquid cooled, the coolant heater must keep the water jacket temperature above 90°F. NFPA 99, 1999 edition 3-188.8.131.52. (Most engines have a closed loop liquid system that adapts very well to coolant heaters.)
Note: Engine temperature is a performance requirement. This applies to all generators.
A Low temperature Alarm
is required in the remote annunciator for all healthcare facilities all the way back to NFPA 76A, 1970 edition. This alarm must come on if the system temperature falls below the parameters listed above. Also, there must be visual indication of a low coolant temperature condition on or near the engine - the control panel would be nice. See NFPA 99, 1999 edition chapter 3-184.108.40.206(a) 1 and look all the way back to NFPA 76A, 1970.
Generators and automatic transfer switches as well as their appurtenant devices employ high voltages that can hurt you. Do not attempt to work with this equipment unless you are qualified. Observe all rules and cautions found in the manufacturer’s manuals as well as NFPA 70E, Standard for Electrical Safety in the Workplace.
The assistance I provide is based on the questions you ask and the accuracy of the information you provide about your equipment or project. I cannot guarantee you will like or agree with my response.
Standby Power Solutions LLC disclaims any liability for any personal injury, property, or other damages of any nature whatsoever, whether special, indirect, consequential or compensatory, directly or indirectly resulting from the publication, use of, or reliance on this document. Standby Power Solutions, LLC also makes no guaranty or warranty as to the accuracy or completeness of any information contained herein. Anyone using this document should rely on his or her own independent judgment, or as appropriate, seek the advice of a competent professional in determining the exercise of reasonable care in any given circumstances.